More than 60% of all reported support calls and problems associated with electronic dispensers arise from poor electrical installation. The reliability and safe efficient function of your LPG station is your life blood. It if does’nt work, you’re losing money. Hours and dollars spent on initial installation and down-time troubleshooting only make the losses greater.
Then add the complexity of multiple sites, each with a different electrician installing, and everyone is different. Standardization and central integration are KEY to reliable and efficient operation. The ParaFOUR P4-SECP series integrated Station Electrical Control Panels, and the solution. Integrating ALL electrical control elements into a single rack or panel mount box, to centralize all control of the station. The Economy line is designed specifically for smaller bottle filling, or single/dual hose Autogas dispensers.
- NEMA 4X fiberglass enclosure -Available in single or three phase, from 2 - 7.5 HP -Compact mounting size 12” x 9” x 9” (Most models -UL listed enclosed motor starter -Galvanized back plane with DIN rail mounted components -Requires properly rated circuit breaker in supply panel (typically20-30 amps. -Motor starter / Disconnect with current limit integrated -Manual reset on overload protection -Through door disconnect, “Lock-Out-Tag-Out” capable -Hooded Emergency Stop Button, breaks ALL power to the station which depressed -Optional “HOA” switch for manual over-ride testing -1-10 second time delay in motor start to delay pump start when opening internal valves - 6 Amp breaker for dispenser, rated for P4-Series dispensers with all options installed -Optional auxiliary 6 Amp breaker for third party card readers -Optional LED Pilot light for run indication -DIN rail mounted terminals for easy connections - All connection points labeled -Satisfies all NFPA and NEC requirements for single point station electrical integration -Prewired and assembled to individual station specifications. Units built to order based on site specifications.